As a transmission line has a specific configuration at an operating voltage, the installation of surge arresters thereof has to take into account the line configuration in order to achieve the best total flash rate. This paper deals with the characteristics in installing surge arresters in the 110 kV and 220 kV transmission lines in Vietnam. Best locations of surge arresters in a given line are determined by studying the effect of main parameters of the transmission lines, such as the type of tower, the number of shield wire, the number of surge arrester to be installed and the footing resistance. The total flashover rate of each transmission line was calculated by the electrogeometric model (EGM) and the electromagnetic transient program simulation (EMTP/ATP), which can be used as a practical guide for the utilities.
224-C1, Hanoi University of Science and Technology 1 Dai Co Viet, Hai Ba Trung, Hanoi, Vietnam Tel: +84 (024) 3623.0949 | email: firstname.lastname@example.org
TẠP CHÍ KHOA HỌC VÀ CÔNG NGHỆ Giấy phép số37/GP-BTTTT (15/01/2021) Giấy phép sửa đổi, bổ sung số140/GP-BTTTT (05/3/2021) Đơn vị cấp phép:Bộ Thông tin và Truyền thông Cơ quan chủ quản:Trường Đại học Bách Khoa Hà Nội Phó tổng biên tập phụ trách:GS. Đinh Văn Phong